In 2022 CMI acquired KennyClamp and was pleased to have it in our product line. KennyClamp has long been manufactured in partnership with CMI and is a complementary addition to CMI’s other electrical products and brands. KennyClamps are now directly manufactured and sold exclusively by CMI.
- Install Kenny Clamp through a 1/2″ Knockout with paint remover, tighten the steel locknut, insert grounding electrode conductor through the Kenny Clamp, and tighten the compression nut. Your installation is NOW CODE COMPLIANT.
- The Kenny Clamp bonds the enclosure of a service panelboard, load center, separately derived system or switchboard to the grounding electrode conductor or to a metallic raceway.
- Complies with 250.64 (E) NEC when entering and exiting metallic raceways and enclosures.
- Assures good metallic connection and low impedance path for grounding and bonding of electrical